Cut to length - sold by the foot. Enter the desired footage in the QTY box.
Minimum 1' to maximum 1000'.
Type SE, Style SER Service Entrance may be used as service-entrance conductors and in other applications where SE cables are permitted when installed as specified by NEC® dry locations at temperatures up to 90°C.
Stranded conductors: Uncoated copper per ASTM-B3, ASTM-B8, and ASTM-B787
Type THHN conductors Black PVC (polyvinyl chloride), rated to 90°C in wet or dry locations Jacketed with black nylon (polyamide) One phase conductor has a red stripe on its insulation surface for easy polarity identification.
White PVC (polyvinyl chloride), rated 90°C Jacketed with white nylon (polyamide)
Equipment Ground Conductor:
Bare stranded copper conductor
Gray, sunlight-resistant PVC (polyvinyl chloride) jacket over the complete assembly
UL 83 (insulated conductors)
UL 854 Service Entrance Cables, File No. 11098
Federal Specification A-A-59544
NFPA70: National Electrical Code
Insulated Conductor Size: 4 AWG
Bare Ground Size: 6 AWG (7)
Outside Diameter: 0.80 inches
Ampacity amps 95 @ 90°C
Net Weight: .585 lbs/ft
*Data provided on this page is subject to change based on different manufacturers variances.