4-4-6 Aluminum SEU Service Entrance Cable
Product DetailsLearn everything you want to know about this product to make an informed purchase
Aluminum SEU cable is primarily used as panel feeder in multiple unit dwellings and for branch circuits. Maximum operating temperature is not to exceed 90°C in wet locations. Voltage rating is 600 volts.
Conductor - Aluminum SEU cable has a compact strand soft drawn 8000 series aluminum conductor, per ASTM B-801
Insulation - Aluminum SEU cable has a type XHHW-2 cross linked polyethylene (XLP) insulation. The conductors are cabled together with an aluminum alloy concentric neutral and covered with a reinforced binder tape.
Jacket - Aluminum SEU cable has a gray sunlight resistance polyvinyl chloride (PVC) jacket.
UL 44, 854
Federal Specification J-C - 30B
Ampacities based on National Electric Code, 2005 edition, section 310-15
60°C when terminated to equipment for circuits rated 100amps or less or marked for 14ga through 1ga conductors
70°C when terminated to equipment for circuits rated over 100amps or marked for conductors larger than 1ga
90°C wet or dry locations For dwelling units, conductors shall be permitted at listed Ampacities to be utilized as 120/240 volt, 3-wire, single phase service conductors that supply the total load
Insulated Conductor Size: 4 AWG
Bare Neutral Size: 6 AWG
Outside Diameter: 0.502 inches
Ampacity: 75 amps @ 90°C
Net Weight: .184 lbs/ft
*Data provided on this page is subject to change based on different manufacturers variances.
|Wire Size||2 AWG|
|Stranded or Solid||Stranded|