XHHW Stranded Building Wire. Cut to length - sold by the Foot.
600 MCM XHHW Building Wire
Product DetailsLearn everything you want to know about this product to make an informed purchase
Cut to length - sold by the foot. Enter the desired footage in the QTY box.
Minimum 10' to maximum 1000'. Please call for longer put ups.
Type XHHW-2/RW90 building wire is intended for general purpose applications utilized in conduit, underground in conduit, or other recognized raceways for services, feeders, and branch-circuit wiring as specified in the National Electrical Code (NEC). Type XHHW-2/RW90 is permitted for 600 volt applications and can be used in wet or dry locations at temperatures not to exceed 90˚C. Suitable for applications requiring low-leaking circuits and a dielectric constant of 3.5 or less.
Available in sizes 14 AWG through 1000 KCMIL. On 250 KCMIL and larger, sequential foot markings located every foot for easy measuring. For 1 AWG through 4/0 AWG, sequential foot markings on master reels only unless otherwise specified. 6 AWG and larger rated Sunlight Resistant in all colors. 1/0 AWG and larger are rated for cable tray use and comply with IEEE 1202/FT4 (70,000 Btu/hr) flame test and ICEA T-29-520 (210,000 Btu/hr) flame test.
Underwriters Laboratories Standard UL-44
ASTM Stranding Class B3, B8, B787
Federal Specification A-A-59544
Canadian Standards Association C22.2 No. 38
NEMA WC-70/ICEA S-95-658
NFPA 70: National Electrical Code (NEC)
UL 1685-FT4/IEEE 1202 (70,000 Btu/hr) Flame Test (1/0 AWG and larger)
ICEA T-29-520 (210,000 Btu/hr) Flame Test
ARRA 2009; Section 1605 "Buy American" Compliant
Stranded, uncoated bare copper conductors per ASTM-B3, ASTM-B787 and ASTM-B8
Cross-linked polyethylene (XLPE) insulation per UL-44
Size: 600 MCM
Number of Strands: 61
Insulation Thickness XLPE: 2.03 mm / 0.080 inches
Outside Diameter: 25.98 mm / 1.023 inches
Weight: 1.960 lbs per ft
Allowable Ampacity: 355 Amps at 60ºC / 420 Amps at 75ºC / 475 Amps at 90ºC
*Data provided on this page is subject to change based on different manufacturers variances.
|Type of Structure||Residential, Commercial, Industrial|
|Wire Size||600 MCM|
|# of Conductors||1 Conductor|
|Conductor Material||Bare Copper|
|Insulation Material||XLPE - Cross-linked Polyethylene|
|Location Use||Wet, Dry|
|Indoor/Outdoor Use||Indoor, Outdoor|
|Applications||General purpose wiring for lighting & power|
|Standards||UL Listed, c(UL) Listed, RoHS Compliant|
|Features||Water Resistant, Oil & Gas Resistant, Heat Resistant, Moisture Resistant|