2-2-2-4 Copper SER Service Entrance Cable. Cut by the foot.
2-2-2-4 Copper SER Service Entrance Cable
Product DetailsLearn everything you want to know about this product to make an informed purchase
Cut to length - sold by the foot. Enter the desired footage in the QTY box.
Minimum 1' to maximum 1000'.
Type SE, Style SER Service Entrance may be used as service-entrance conductors and in other applications where SE cables are permitted when installed as specified by NEC® dry locations at temperatures up to 90°C.
Stranded conductors: Uncoated copper per ASTM-B3, ASTM-B8, and ASTM-B787
Type THHN conductors Black PVC (polyvinyl chloride), rated to 90°C in wet or dry locations Jacketed with black nylon (polyamide) One phase conductor has a red stripe on its insulation surface for easy polarity identification.
White PVC (polyvinyl chloride), rated 90°C Jacketed with white nylon (polyamide)
Equipment Ground Conductor:
Bare stranded copper conductor
Gray, sunlight-resistant PVC (polyvinyl chloride) jacket over the complete assembly
UL 83 (insulated conductors)
UL 854 Service Entrance Cables, File No. 11098
Federal Specification A-A-59544
NFPA70: National Electrical Code
Insulated Conductor Size: 2 AWG
Bare Ground Size: 4 AWG (7)
Outside Diameter: 0.970 inches
Ampacity amps 125 @ 90°C
Net Weight: .899 lbs/ft
*Data provided on this page is subject to change based on different manufacturers variances.
|Cable Type||Service Entrance Cable|
|Wire Size||2 AWG|
|# of Conductors||3 Conductors w/ Ground|
|Conductor Material||Bare Copper|
|Stranded or Solid||Stranded|
|Insulation Material||PVC - Polyvinyl Chloride|
|Jacket Material||PVC - Polyvinyl Chloride|
|Location Use||Wet, Dry|
|Indoor/Outdoor Use||Indoor, Outdoor|