14/2C Type MC-HL Aluminum Armored Cable w/ PVC Jacket - 1#14 Ground Wires
Control and lighting circuits in manufacturing and processing plants, feeders in industrial and commercial distribution systems. May be directly buried or installed in cable tray or raceway.
Class B stranded, bare, annealed copper per ASTM B-3 and B-8
Cross-Linked Polyethylene (XLP) meeting the requirements of ICEA S-95-658 (NEMA WC70) and Type XHHW requirements of UL, color coding is Method 1, Table E-2
The insulated conductors and a single, uninsulated UL ground wire(s) are cabled with fillers to make round
An impervious, corrugated continuous seam-welded aluminum alloy sheath in accordance with UL 1569. Armor is pressure-tested and meets the grounding requirements of NEC Article 250
Black, sunlight-resistant Polyvinyl Chloride (PVC)
Based on not more than three conductors in raceway or cable or earth and an ambient temperature of 30°C per NEC table 310.16. All multiconductor values have been derated per 2008 NEC Table 310.15(B)(2)(a) – TEMPERATURE: 90
Cables are UL listed for cable tray use and meet the IEEE 1202 (70,000 Btu/hr) flame test. Individual conductors and completed cables are tested in accordance with UL 2225 requirements for Type MC-HL cables
Size: 14 AWG
Conductor: 2 Conductor
Ground Wires: 1 #14AWG
Outside Diameter: 0.640 inches
Ampere Rating: 25
Weight: 0.180 lbs per ft.
*Data provided on this page is subject to change based on different manufacturers variances.